Electric Energy Recovery Equipment for Diesel Engine Load Test
The 6000kW electric energy recovery equipment for diesel engine load test is the high-power 4Q recification researched and produced by our company to meet the electric energy recovery demands of diesel engine load tests. It adopts the “common DC bus multi contravariant power panel parallel technical scheme”, which has the characters like good performance, reliable functioning, compact structure, convenient use and preservation, etc., and it is the best choice for the electric energy recovery in high-power diesel engine load tests.
The functions of 6000kW electric energy recovery equipment for diesel engine load test made by CenteRole (Dalian) Electric Transmission Technology Co., Ltd. are divided into rectification, DC chopping boosting, contravariant, alternating boosting and resistive load. The rectification part of the electric energy recovery equipment is realized by a panel, the electric energy recovery equipment is equipped with 2 sets of DC chopping boosting, contravariant and alternating boosting systems, each system has a DC switch panel, 3 contravariant panels, 1 boosting transformer and 1 alternating high-voltage board. The resistive load part consists of a DC switch and a load resistor panel.
When the diesel engine drives the synchronous generator to operate, the 3-phase alternating voltage output by the synchronous generator will be converted to DC voltage through the rectifying panel. The contravariant power panel consists of 2 parts, the boosting chopper circuit and the 3-phase inverter circuit, the former raises the lower DC voltage output by the rectifying panel at any rotation speed to 1000V constant middle DC voltage through the pump, and the latter reverses the 1000V middle DC voltage into the 560V 3-phase sine alternating voltage synchronous with the power grid, and feed it back to the 10kV power grid through the output boosting transformer.
The output current of contravariant power panel can be adjusted by controlling the target output voltage of the boosting chopper circuit, and then control the load inflicted on the diesel engine.
When there is reversed voltage in the power grid system, it will automatically turn on the load resistance and reduce the power that is fed back to the power grid.
When the input DC voltage is lower than 360V, it automatically connects to the load resistance to guarantee that the diesel engine load test is conducted constantly.
When there is fault in one or several contravariant power panels, the input DC contactor in the contravariant power panel will automatically disjunction, and the rest contravariant power panels keep operating normally, and the electric energy recovery device can still constantly operate under the power reducing condition.
ADD： 98 East Tieshan Road, Dalian Economic
and Technical Development Zone, Dalian,
P. R. China